User manual PANASONIC CS-TE35TKEW
DON'T FORGET : ALWAYS READ THE USER GUIDE BEFORE BUYING !!!
If this document matches the user guide, instructions manual or user manual, feature sets, schematics you are looking for, download it now. Diplodocs provides you a fast and easy access to the user manual PANASONIC CS-TE35TKEW. We hope that this PANASONIC CS-TE35TKEW user guide will be useful to you.
Manual abstract: user guide PANASONIC CS-TE35TKEW
Detailed instructions for use are in the User's Guide.
[. . . ] Order No: PAPAMY1703052CE
Indoor Unit CS-TE20TKEW CS-TE25TKEW CS-TE35TKEW CS-TE42TKEW
Outdoor Unit CU-TE20TKE CU-TE25TKE CU-TE35TKE CU-TE42TKE Destination Europe Turkey
Please file and use this manual together with the service manual for Model No. WARNING
This service information is designed for experienced repair technicians only and is not designed for use by the general public. it does not contain warnings or cautions to advise non-technical individuals of potential dangers in attempting to service a product. Products powered by electricity should be serviced or repaired only by experienced professional technicians. [. . . ] These shifting processes are depending on the air conditioner settings and the operation environment. The final shifted value will be used as internal setting temperature and it is updated continuously whenever the electrical power is supplied to the unit. When compressor is OFF (Thermostat OFF) and AUTO FAN is set, the fan will stop periodically. Compressor is ON after waiting for 3 minutes, if the Intake Air Temperature - Internal Setting Temperature > Compressor OFF point. Soft Dry Operation Thermostat control
Compressor is OFF when Intake Air Temperature - Internal Setting Temperature < -2. When compressor is OFF (Thermostat OFF) and AUTO FAN is set, the fan will stop periodically. Compressor is ON after waiting for 3 minutes, if the Intake Air Temperature - Internal Setting Temperature > Compressor OFF point. Compressor is ON after waiting for 3 minutes, if the Intake Air Temperature - Internal Setting Temperature < Compressor OFF point. During operation mode judgment, indoor fan motor (with speed of Lo-) is running for 30 seconds to detect the indoor intake air temperature. For the 2nd judgment onwards o If indoor intake temperature - remote control setting temperature ≥ 3°C, if previous operate in DRY mode, then continue in DRY mode. Fan motor’s number of rotation is determined according to remote control setting. remote control Tab ○ Hi ○ Me ○ Me○ Lo ○ QLo
[Heating] Fan motor’s number of rotation is determined according to remote control setting. remote control Tab ○ SHi ○ Me ○ Me○ Lo ○ QLo
ii Auto Fan Speed [Cooling , Dry] According to room temperature and setting temperature, indoor fan speed is determined automatically. When set temperature is not achieved, the indoor fan will operate according to pattern below. fan Speed Higher Medium Lower a b c d e f g [1 pattern : 10 s] h a b
When set temperature achieved, the indoor fan speed will be fixed. According to indoor pipe temperature, automatic heating fan speed is determined as follows. Immediately after the fan motor started, feedback control is performed once every second. During fan motor on, if fan motor feedback ≥ 2550 rpm or < 50 rpm continue for 10 seconds, then fan motor error counter increase, fan motor is then stop and restart. If the fan motor counter becomes 7 times, then H19 - fan motor error is detected. 3 Outdoor Fan Motor Operation
Outdoor fan motor is operated with one fan speed only. It starts when compressor starts operation and it stops 30 seconds after compressor stops operation. oN Compressor: ON Outdoor Fan:
ON OFF Fan Speed OFF ON
During cooling operation, and outdoor ambient temperature is below 8°C, outdoor fan speed will be controlled according to outdoor piping temperature as following:
OD Pipe Temperature A B 26°C 33°C
During above condition, when indoor heat exchanger temperature is below 5°C, the outdoor fan will stop according to outdoor piping temperature as following:
AMP Air Conditioning www. [. . . ] During operation of cooling and heating, when compressor tank temperature data (112°C) is detected by the compressor tank temperature sensor. 2/3 way valve closed During operation of cooling and heating, when an input over-current (X value in Total Running Current Control) is detected by checking the input current value being detected by current transformer (CT) with the compressor running. 28 F99 (DC Peak Detection)
Malfunction Decision Conditions During startup and operation of cooling and heating, when inverter DC peak data is received by the outdoor internal DC Peak sensing circuitry. Disassembly and Assembly Instructions
WARNING High Voltage is generated in the electrical parts area by the capacitor. [. . . ]
DISCLAIMER TO DOWNLOAD THE USER GUIDE PANASONIC CS-TE35TKEW
Click on "Download the user Manual" at the end of this Contract if you accept its terms, the downloading of the manual PANASONIC CS-TE35TKEW will begin.